No. The vent requires a minimum of one-inch clearance to all combustible material. For severe problems such as cold attics, contact the Technical Services Department of the manufacturer for alternative solutions.
AmeriVent Flashings are made from .018 inch, 26 gauge, G90 galvanized steel, as are the firestops and the outer wall of the vent sections.
A Type B Gas Vent elbow is not designed to carry any load, therefore, whenever an elbow or offset is used, it must be resupported.
First, a metal firestop must be used at each floor level that the vent passes through, with the exception of the roof level where no firestop is required. Secondly, the firestop should always be located at the bottom surface of each floor level except for the upper floor where the firestop should be installed on top of the joist areas in the attic.
The rules may vary from area to area, and you should always check with the local building inspector. With the appliances used today, the use of an excessive number of elbows can cause condensation problems. Try to limit the installation to no more than two 90 offsets and to use offsets of no more than 45 wherever possible.
Yes. There is a correct direction, and each section is marked with an 'up' arrow that shows the proper orientation, or direction of the section, which is always away from the appliance.
No! Because the AmeriVent snap-lock locking system cannot be accidentally unlocked, unlike other types of cap locks, the Ameri-Cap will never blow off in strong winds.
No, the two walls are spot welded together at the top of each section, and therefore, the air inside cannot rise because the space is dead air space.
With the patented AmeriVent Ameri-Cap, the system can be installed on most roofs with an outlet at a minimum of one foot above the roof. It is important that the installer read the Termination Section of the Installation Instructions and the local building codes to check for exceptions.
AmeriVent components are made from materials unsurpassed in the gas vent industry and should last as long as the heating system in your home. The inner wall is made from a highly corrosion resistant aluminum alloy and the outer wall is made of a hot dipped galvanized steel that meets or exceeds all UL requirements.
AmeriVent Type B Gas Vent Systems can be supported by two of the easiest to use support systems in the industry today: 1-The Ameri-Bucket Support or 2-The Firestop Support Plate Assembly-both of which are Underwriters Laboratories listed. In addition, field-fabricated supports may be used. Consult your local building codes for applicable regulations regarding field-fabricated supports.
No. Type B Gas Vent can only be used on gas fired equipment-either natural gas or LP gas.
No. Because the Type B Gas Vent system is tested and listed by Underwriters Laboratories for safety, it doesn't need a fire rating. The material for the outside wall is the same as that required for a firestop.
No. Drywall and wallboard are considered combustible materials and should not be installed against the vent including the use of this material to close off the hole around the vent. Type B Gas Vent requires a minimum of one-inch clearance to combustibles. This one-inch is a typical clearance for all brands of Type B Vent, but each section of vent pipe is marked with the clearance required by Underwriter Laboratories, so it should be checked.
Not at all. The lock at the bottom end of each AmeriVent section has three locking teeth marked with an embossed dot. Simply pry out the three locking teeth and twist the sections. They come apart easily. To reuse the section, push the teeth back in, and it's ready to install.
Sometimes, vent systems with a twist-lock or the type of lock requiring a locking band can come apart when putting a flashing on the roof or when you are adjusting an elbow. Be assured, AmeriVent's snap-locking system will not come apart unless you want it to. There's no need to worry about the possibility that when you are working on one part of the AmeriVent system that you might unlock a section somewhere else.
There are a number of connecting methods used by gas vent manufacturers. We believe that the AmeriVent® Type B Gas Vent system, manufactured by American Metal Products, is the easiest vent to assemble on the market today. The patented snap-lock locking system allows assembly by just pushing the sections together until you hear a 'click.' There are no male and female openings to line up or locking brackets to worry about-just push and snap the sections together.
Type B Gas Vent is not rated for a specific temperature level, but this type of product should only be used on gas-fired equipment that has a draft hood or that was tested and listed for use with Type B Gas Vent systems. This type of equipment, such as furnaces, heaters, and water heaters, typically has an outlet temperature in the 400 F plus room temperature range. However, even if the temperature is correct, the instructions for the equipment should be checked to make sure it was tested for use with Type B Gas Vent.
Type B Vent is an Underwriters Laboratories' designation for product tested under the UL 441 Testing Standard. It's a type of two-wall, air insulated, venting system that is used for gas burning appliances and is tested and listed by UL for safety.